The most recent service of the vending machine was done on March 7, 2017. The T.D.S. (total dissolved solids) results were: County Water 130 PPM. Purified Water 6 PPM. This is a 95 % rejection percentage; excellent quality. The pH of the alkalized water tested at 9+. During the service the 20” pre carbon, Big Blue Radial Flow pre-carbon, both of the 10” post carbon filters and the Ultra Violet lamp were changed. The entire unit, including the dispensing box and the interior of the vending machine, was cleaned and disinfected. This machine is serviced every two months to insure excellent quality.
9-6-17 TDS RAW-130, TDS PRO-4, REJECTION-98, PH9+
4-19-17 TDS RAW-150, TDS PRO-8, REJECTION-95, PH9+
3-7-17 TDS RAW-130, TDS PRO-6, REJECTION-95, PH9+
4-13-16 TDS RAW-130, TDS PRO-4, REJECTION-98, PH9+
1-13-16 TDS RAW-110, TDS PRO-4, REJECTION-99,PH9+